Remote Control of gas consumption.
|Manage the end user. For safety reasons, domestic and office gas meters are equipped with a gas analyzer with a shut-off valve. Installing the radio module D100FC at the counter, equipped with such a valve, allows not only to obtain the data, but also to control the consumption of gas.|
|The radiomodule D100FC can be equipped with Adapter AD220/50 to control the pulse gas valve with manual reset (opening) and remote shutdown. The adapter allows you to control the valve with connection diameters DN15, DN20, DN25, with operating voltage of 230V control coils and power consumption up to 11W/11 VA, for example, of the company MADAS.
For installing the Adapter AD220/50 radio D100FC contained in document AD220_50_Valve_control_adapter_en. There is also a recommendation on how to connect the adapter together with the gas analyzer, and in the case of connection of the valve in his absence.
|The radiomodule D100FC can be equipped with Adapter AD12/1000 to control normally open pulse gas valve with manual reset (the opening) and remote shutdown. The adapter allows you to control the valve with connection diameters DN15, DN20, DN25, with an operating voltage of 9-12V and the control pulse current to 1A.
Use of the valve with a working voltage of 9-12V and adapters AD12/1000 eliminates the external power supply or 220V AC voltage and used as a power source battery radio module.
|The radiomodule D100FC, complete with valve control adapter allows the operator with appropriate permissions to remotely turn off the gas consumption in the event of emergencies – such as leaks, or in the case of non-payment of. Turning ON gas is made by hand, worker of gas supply organization. Debtors can be transferred to the regime of prepaid gas consumption. It is a good alternative to prepaid gas meters.|